MidNite Solar19115 62nd Ave NE
Arlington, WA 98223
Wind and Hydro
Product: MNEPV 80A or 100A
MidNite's breakers are rated to break the full rated load at the rated voltage repeatedly, with NO DAMAGE. Always use a properly sized breaker for disconnecting.
Read about the 165 VDC ETL TEST STORY
MNEPV breakers are the same as CBI QY breakers except the standard used is inadequate for the solar industry. MidNite breakers have been evaluated by ETL to 150VDC and are listed for US and Canada. All of the NRTL listings still apply. Breakers ordered under the CBI part numbering system will not be listed for 150VDC and in many cases are not suitable for the solar industry.
Accepts up to #2 wire.
Breaker Torque Value: 20 In-Lbs (2.3NM)
All MidNite circuit breakers can be used at 100% rated current when mounted in a MidNite enclosure.
California Residents: Warning
Description:80 or 100 amp Din rail mount breaker.
Size: Width 1 inch (26mm) Wire size up to 2 AWG
Weight: 1 Lb/s
price increase 9-1-21